An engine-generator is the combination of an electrical generator and an
engine (prime mover) mounted together to form a single piece of equipment. This
combination is also called an engine-generator set or a gen-set. In many
contexts, the engine is taken for granted and the combined unit is simply called
Components[Back to Contents]
In addition to the engine and generator, engine-generators generally include a fuel supply, a constant engine speed regulator (governor) and a generator voltage regulator, cooling and exhaust systems, and lubrication system. Units larger than about 1 kW rating often have a battery and electric starter motor; very large units may start with compressed air either to an air driven starter motor or introduced directly to the engine cylinders to initiate engine rotation. Standby power generating units often include an automatic starting system and a transfer switch to disconnect the load from the utility power source when there is a power failure and connect it to the generator.
Types[Back to Contents]
Engine-generators are available in a wide range of power ratings. These
include small, hand-portable units that can supply several hundred watts of
power, hand-cart mounted units, as pictured below, that can supply several
thousand watts and stationary or trailer-mounted units that can supply over a
million watts. Regardless of the size, generators may run on gasoline, diesel,
natural gas, propane, bio-diesel, water, sewage gas or hydrogen.Most of the
smaller units are built to use gasoline (petrol) as a fuel, and the larger ones
have various fuel types, including diesel, natural gas and propane (liquid or
gas). Some engines may also operate on diesel and gas simultaneously (bi-fuel
Many engine-generators use a reciprocating engine, with fuels mentioned above. This can be a steam engine, such as most coal-powered fossil-fuel power plants use. Some engine-generators use a turbine as the engine, such as the industrial gas turbines used in peaking power plants and the microturbines used in some hybrid electric buses.
The generator voltage (volts), frequency (Hz) and power (watts) ratings are selected to suit the load that will be connected.
Engine-driven generators fueled on natural gas fuel often form the heart of small-scale (less than 1,000 kW)combined heat and power installations.
There are only a few portable three-phase generator models available in the US. Most of the portable units available are single-phase generators and most of the three-phase generators manufactured are large industrial type generators. In other countries where three-phase power is more common in households, portable generators are available from a few kW and upwards.
Portable engine-generators may require an external power conditioner to safely operate some types of electronic equipment. Small portable generators may use an inverter. Inverter models can run at slower RPMs to generate the power that is necessary, thus reducing the noise of the engine and making it more fuel-efficient. Inverter generators are best to power sensitive electronic devices such as computers and lights that use a ballast.
The mid-size stationary engine-generator pictured here is a 100 kVA set which
produces 415 V at around 110 A. It is powered by a 6.7 literturbocharged Perkins
Phaser 1000 Series engine, and consumes approximately 27 liters of fuel an hour,
on a 400 liter tank. Diesel engines in the UK can run on red diesel and rotate
at 1,500 or 3,000 rpm. This produces power at 50 Hz, which is the frequency used
in Europe. In areas where the frequency is 60 Hz (United States), generators
rotate at 1,800 rpm or another divisor of 3600. Diesel engine-generator sets
operated at their peak efficiency point can produce between 3 and 4 kilowatt
hours of electrical energy for each liter of diesel fuel consumed, with lower
efficiency at partial loads.
Many generators produce enough kilowatts to power anything from a business to a full-sized hospital. These units are particularly useful in providing backup power solutions for companies which have serious economic costs associated with a shutdown caused by an unplanned power outage.For example, a hospital is in constant need of electricity, because several life-preserving medical devices run on electricity, like ventilators.
A very common use is a railway diesel electric locomotive, some units having over 4,000 hp (see diesel generator).
Large generators are also used onboard ship that utilized a diesel-electric powertrain.
Applications[Back to Contents]
Engine-generators are used to supply electrical power in places where utility (central station) power is not available, or where power is needed only temporarily. Small generators are sometimes used to supply power tools at construction sites. Trailer-mounted generators supply power for temporary installations of lighting, sound amplification systems, amusement rides etc.
Trailer mounted generators or mobile generators, diesel generators are also
used for emergencies or backup where either a redundant system is required or no
generator is on site. To make the hookup faster and safer, a tie in panel is
frequently installed near the building switchgear that contains connectors such
as camlocks. The tie in panel may also contain a phase rotation indicator (for 3
phase systems) and a circuit breaker. Camlock connectors are rated for 400 amps
up to 480 volt systems and used with 4/0 type W cable connecting to the
generator. Tie in panel designs are common between 200 to 3000 amp
Standby power generators are permanently installed and kept ready to supply power to critical loads during temporary interruptions of the utility power supply. Hospitals, communications service installations, data processing centers, sewage pumping stations and many other important facilities are equipped with standby power generators. Some standby power generators can automatically detect the loss of grid power, start the motor, run using fuel from a natural gas line, detect when grid power is restored, and then turn itself off—with no human interaction.
Privately owned generators are especially popular in areas where grid power is undependable or unavailable. Trailer-mounted generators can be towed to disaster areas where grid power has been temporarily disrupted.
Safety[Back to Contents]
It is important to prevent backfeeding when turning on a portable engine generator, which can harm utility workers or people in other buildings. Before turning on a diesel- or gasoline-powered generator, users should make sure that the main breaker is in the "off" position, to ensure that the electric current does not reverse.
Operation of portable electric generators must occur in well ventilated spaces to prevent carbon monoxide poisoning.
Exhausting extremely hot flue gases from gen-sets can be done by factory-built positive pressure chimneys (certified to UL 103 test standard) or general utility schedule 40 black iron pipe. It is recommended to use insulation to reduce pipe skin temperature and reduce excessive heat gain into the mechanical room. There are also excessive pressure relief valves available to relieve the pressure from potential backfires and to maintain the integrity of the exhaust pipe.
Kinds[Back to Contents]
- Diesel electric locomotive
- Diesel generator
- Diesel electric multiple unit
- Head end power